Then the ambient fan moves cool air from near the bottom of the heat exchanger through the core where the heat from the enclosure is absorbed and dissipated to the ambient air out of the top of the heat exchanger. HE Series Heat Exchangers provide from 5.7 to 83 watts/degree Fahrenheit of closed-loop heat removal capacity and are available in a
DC HEX 120W/oK with for an example 15oC temperature differential between in and outdoor air temperature gives a passive cooling capacity of 1800W/h and the HEX DC fans on this size will only have a power consumption of 180W/h vs normal active AC air conditioner mode that will have a power consumption of 1130W/h to produce 3000W cooling capacity.
DC48V 180W/K Enclosure Heat Exchanger / 1800W HEX High quality DC48V 180W/K Enclosure Heat Exchanger / 1800W HEX With LED Display Dry Contact Alarm Output Remote Control from China, China's leading cabinet heat exchanger product, with strict quality control electric heat exchanger factories, producing high quality electric heat exchanger
Heat Pipe Heat Exchanger uses refrigerant phase-change heat transfer principle to conduct passive cooling to cabinet equipment compartment. It makes full use of temperature difference between cabinet internal environment and external environment, effectively introduce the external cold air, fast move heat inside the station to the outer environment, to realize cabinet cooling.
Enclosure Heat Exchanger - Outdoor Telecom CabinetDC48V 180W/K Enclosure Heat Exchanger / 1800W HEX With LED Display Dry Contact Alarm Output Remote Control. Cooling Method:heat pipe, passive cooling. Input voltage:DC-48V±20%. Cooling capacity L35/L35:180W/K (1800W) Power consumption L35/L35:210W/K. Contact Now.
·Outdoor telecom ·Data networking Heat Exchanger Type Air-to-Air Heat Exchangers Liquid-to-Air Heat Exchangers Cooling Unit) Passive heat radiates through enclosure walls. Cool air environment configurations and can be equipped with either AC or DC fans. * This heat exchanger is custom designed for a specific
Quality Outdoor Telecom Cabinet & Outdoor Battery DC48V Outdoor Telecom Enclosure Heat Exchanger 400 Watt Top Mounted HE06-40SEH/T 650W Industrial Electrical Enclosure Heat Exchanger , Mixed Working Fluid Heat Exchanger Side Mounted Outside Cabinet Intelligent Ventilation System IVS With Four Fans
Apr 05, 2016 · Heat exchangers are a more cost efficient method of cooling an enclosure than air conditioners, but they can only be used in situations where the ambient temperature remains below the maximum operating temperature of the equipment. Cooling System Size. The correct size of a telecom enclosure cooling system will depend on several factors.
Thermal Management of Outdoor Enclosures, Part 4:Passive May 31, 2018 · This part will focus on passive cooling systems available to the thermal telecom engineer when designing the thermal management system for a new indoor/outdoor enclosure. Passive cooling systems are those that require no external power and possess no moving parts. Figure 1 shows a typical cabinet with a passive cooling unit (a wall finned on
Heat Pipe Heat Exchanger uses working fluid phase-change heat transfer principle to conduct passive cooling to cabinet equipment compartment. It makes full use of temperature difference between cabinet internal environment and external environment, effectively introduce the external cold air , fast move heat inside the station to the outer environment, to realize cabinet cooling.
Proud to be serving the Machining Platform you can trust