Jun 01, 1997 · In this study, tests with and without a thermosyphon or gravity-assisted wickless heat pipe heat exchanger (HPHE) were carried out on a Hilton air-conditioning unit. The HPHE was constructed as shown in Fig. 2, with parameters as follows:Themosyphon tubes:D 15.88 mm seamless pure copper, 38.1 mm between the tube centres across the face, 33.0 mm between row centres; 24 tubes in total.
Cabinet Cooler Units - Heat PipesHeat sink and heat pipe coolers operate by the same principle, but use different means of achieving heat reduction. They use a heat exchanger, either a heat sink or a heat pipe, that captures heat from the air inside the unit and transfers it to the outside air. It then recirculates the cooled air
reheat applied to the supply air stream. The heat pipe can only reheat with as much energy as is extracted from the air on the precool side. Therefore, if a heat pipe system is selected for a hot day, the heat pipe will underperform on a cool day when the entering heat energy is lower and supply colder air than is needed to the space.
ENERGY RECOVERY VENTILATION - Home Page for Heat pipes are usually constructed of copper tubes with aluminum fins. Tubes are installed horizontally, but tilting the tubes one direction or the other can control the amount of heat transfer. For instance, operating the heat pipe unit with the evaporator end lower than the condenser end improves the liquid refrigerant flow back to the evaporator and increases heat transfer capacity. Reversing the
Engineered Air's HRA Series is an energy recovery package specifically designed to reduce the high costs of conditioning ventilation air by recovering a significant portion of the thermal energy from the exhaust air. Application Air to air heat exchangers can be employed in any ventilation system to reduce energy consumption.
HVAC Heat Pipe Energy Recovery ACT Advanced Cooling Energy Recovery. ACT-HP-AAHX is a counter-flow heat exchanger-energy recovery system that features ACTs high-performance, high-reliability heat pipes. Save energy by pre-cooling or pre-heating your incoming building supply air. The system features:
Mar 01, 2007 · The experimental apparatus has been designed and constructed as shown in Fig. 1.The test section consists of two air ducts of 0.3 × 0.22 m 2 section areas connected together by finned tubes heat pipe heat exchanger. A square hole of 0.3 × 0.3 m 2 was made in one side of the two ducts for heat pipe heat exchanger installation. A laboratory refrigeration machine consisting of evaporator
REFRIGERANT AND WATER HEAT PIPESHEAT PIPES AS APPLIED TO AIR CONDITIONING The cooling coil in the standard air conditioner provides both sensible and latent cooling.The following chart shows how the heat pipe provides pre-cooling before the cooling coil.This then increases the latent cooling ability of the coil before the heat pipe re-heats the air back up to a comfortable condition.
Sep 01, 2016 · Instead of a cooling coil, they incorporated a waterair heat exchanger to heat the air after the condenser section and before the evaporator section of the HPHE. They obtained heat transfer coefficients of 1040 and 2050 W/m 2 K for evaporator and condenser sections, respectively. Their results show that the THPHE can replace a water-cooled heat exchanger without loss of performance.
Proud to be serving the Machining Platform you can trust